Model No: 310
Storagetech™’s Model 310 End of Line Deflagration Type Flame arrestors are passive devices that prevent the propagation of a flame or fire from entering into an opening in a pipeline or vessel discharging flammable vapour. The flame cell, under normal operation, allows the free flow of vapour, although it does introduce some additional pressure-loss that must be considered in the design of the system. In a situation where a fire occurs external to the equipment and ignites the vapour, the flames will start to travel back through the system. The flame arrestor will prevent the flame from entering the opening.
This deflagration flame arrestor is suitable for quenching subsonic flames and should be located at the end of a pipeline or exit from a vessel. It should be installed in the horizontal plane and is not for use with pressure relief valves or pressure-vacuum relief valves. A cap and screen protects the vent and restricts dust, wind, rain, or insects from entering and degrading the efficacy of the product. The unit is supplied with an earth point, copper tag and cable. Cap has a special opening mechanism, which allows opening automatically after certain time and temperature, so fire flies freely to minimize the effect.
The cell can be removed for cleaning or replacement.
|Sizes:||1” to 12” DN25 to DN300|
|Body/flanges:||Carbon steel, Stainless steel AISI 316 –L or 304-L, Aluminiu, Customer Specification|
|Flange drilling:||API Class 150, PN16, and Special|
|Flame cell:||Stainless steel AISI 304|
|O-ring seal:||Nitrile, Special|
|Cap:||Carbon steel, stainless steel or aluminium.|
|Cover:||Carbon steel, stainless steel or aluminium.|
|Paint finish:||Powder Coating, Colour RAL 9006, Epoxy Paint, Colour RAL 9006, Customer Specification|
|ATEX cert:||Ex II 1/2 G IIB|
Design & Manufacturing Specifications
The size of the vent should be calculated in accordance with API Standard 2000 (ISO 28300)
– Venting Atmospheric and Low-Pressure Storage Tanks or other international standards.